This control panel is designed for the arrangement of centralized and autonomous protection
The product attributes of FIRE ALARM CONTROL PANEL has not been provided.
Packaging & Delivery
Detailed introduction to FIRE ALARM CONTROL PANEL:
This control panel is designed for the arrangement of
centralized and autonomous protection of various objects against
fire by the 24-hours control of the status up to 4 fire alarm
The control panel conforms to all the norms of DSTU EN54-2:2003
and DBN V 2.5-13-98.
The control panel controls and reflects with optical indicators
alarm statuses (alarm loops): the standby mode, the verification of
an alarm loop (if AL is with verification), “Fire”,
“Short-circuit”, “Open-circuit”, “AL switched-off”.
The device controls and reflects with optical indictors the
following kinds of faults and statuses:
The short-circuit of output switches;
The open-circuit of output switches’ loads “Light/Sound”,
“Fire” and “Fault”;
The absence of power voltage of output switches and AL;
The absence of A.C. mains 220 V;
The critical discharge or the absence of a storage
The fault of a charger;
A system error.
The protection against an unsanctioned access inside a case is
provided in the device (opening or breaking of the cover). When
opening the cover, a tamper button activates and the device passes
to the “Alarm” mode.
The device is meant for the connection of 2- and 4-wire alarm
loops. The connection both active and passive detectors is possible
as well as the combined connection of detectors.
The device provides:
Automatic charging of a storage battery and the protection
against its improper connection;
Protection of all the output switches against the short-circuit
with automatic restoration of the initial status after the
elimination of the short-circuit;
Multilevel access to management functions.
With the help of a built-in keyboard it is possible to programme
the following parameters and functions:
The survey and determination the type of alarm loop zone
Fixation of the basic current of AL;
Setting of consumer rights for the management of AL;
Change of consumers’ and an engineer’s passwords;
Setting of an operational mode of a light-sound detector;
Setting of activation time of a light-sound detector;
Setting of a mode and programming of operation logics of
additional output switches;
Reset to factory settings.
Basic Company Information
Manufacturing & Processing Machinery > Metal Processing Machinery
Notice:The above information is provided by members themselves who shall take full responsibility for the authenticity, accuracy and legitimacy of the information. forbuyers.com shall not be liable for that. To avoid the trading risk, please confirm the supplier's qualification and product quality before placing your order. Also, business license approved suppliers are recommended.